In the 1960's the inventor of the Suns-N-Flood Tamer, W. J. Baumbach constructed a clear pipe plumbing system on the outside wall of his workshop in Arlington Virginia. It consisted of a Water Closet, and a Sink Basket drain. A helper climbed up on to the roof and poured buckets of water with red dye down the vent stack to simulate a sewer system backing up which included soap suds. The film first shows the plumbing system backing up and over flowing without the Suns-N-Flood Tamer installed, Then a Suns-N-Flood Tamer is installed in the Water Closet and it shows that it stops the water from over flowing out of the Water Closet and the fact it holds the water back under a 5 foot column of water pressure. Then soap suds are added to the water to show how the Suns-N-Flood Tamer not only holds back the water but also soap suds. The last part of the film shows large quantities of toilet paper being flushed down the Water Closet to demonstrate the fact that the Suns-N-Flood Tamer does not in any way interfere or restrict the flow of water, as a mater of fact the Suns-N-Flood Tamer can stretch and expand larger then the pipe it is installed in. The numbers 1, 2, 3, 4, 5, etc on the vent stack mark how many feet above the flood rim of the Water Closet the water is.
The film was originally done in the 1960's with a color 8mm silent film camera. In the 1990's it was converted to a VHS video, and now on 08-22-2007 a digital version of the original 1960's film can be viewed online. 640x480 28megs here and a 320x240 12meg version here
Installation of Sink Waste Check Valve
(A) Always mount check valve in vertical position.
(B) If practical, do not allow check valve to extend into trap below the normal level of standing water.
(C) Make up slip joint nuts hand tight around check valve.
(D) Always use cross bars with disposals.
(E) Sink Waste Check Valve may be installed on tub waste tee if desirable.
(A) mount check valve in tail piece and install below basket cross bars.
(B) In double compartment sinks, mount check valve under tee, with cross bars, or under each basket.
(C) do not use cross bars provided with check valve when the top of the valve will set less then one inch below baskets cross bars.
(A) Install 1-1/2" solder bushing or slip coupling and tail piece.
(B) Mount check valve in tail piece and install with 1-1/2" slip joint nut.
(C) Always use cross bars with disposals.
(A) Install 1-�" X 1-1/2" solder bushing or slip coupling and tail piece..
(B) Mount check valve in tail piece and install 1-1/2" slip joint nut.
(C) Use 1-1/2" trap.
Installation of Water Closet Check Valve
1. Placing Check Valve
(A) Turn bowl upside down on floor.
(B) Thread a piece of string (approx. 12") through holes in lip of check valve.
(C) Place check valve over horn of bowl.
(D) Fish lower ends of string through closet bolts holes.
2. Placing foam gasket
(A) Pull upper end of string through gasket.
(B) Set gasket over horn outside of check valve.
3. Securing check Valve And Gasket
(A) Knot both strings outside of bowl.
(B) If wax seal is used for gasket, dry bottom of bowl and spread some wax under check valve to secure for installation.
4. Setting Bowl
(A) Set bowl in normal manner.
(B) Check valve will extend through center of flange and opening.
(C) Remove strings after bowl is set.
October 13, 2010